Guide For In-Service Maintenance And Electrical Testing Of Live-Line Tools - The best free software for your
This guide provides recommendations for in-service inspection, maintenance, and electrical testing of live-line tools. These selected comprehensive recommendations. 'OSHA Regulation for In-Service Maintenance and Electrical Testing of Live-Line Tools'. Institute of Electrical and Electronics Engineers Guide for In.
Excerpts from the "OSHA Regulation 2. CFR Part 1. 91. 0 for In- Service Maintenance, Conditioning, and Electrical Testing of Live- Line Tools"Excerpts from the.
Get this from a library! IEEE guide for in-service maintenance and electrical testing of live-line tools. [IEEE Power Engineering Society. Transmission and. IEEE STANDARD. 978-1984 - IEEE Guide for In-Service Maintenance and Electrical Testing of Live-Line Tools.
CFR Part 1. 91. 0 - Federal Register Vol 5. No. 2. 0, 1- 3. 1- 9.
Section 2: Condition of Tools.(i) Each live- line tool shall be wiped clean and visually inspected for defects before use each day.(ii) If any defect or contamination that could adversely affect the insulating qualities or mechanical integrity of the live- line tool is present after wiping, the tool shall be removed from service and examined and tested according to paragraph (i)(2)(iii) of this section before being returned to service.(iii) Live- line tools used for primary employee protection shall be removed from service every two years and whenever required under paragraph (i)(2)(ii) of this section for examination, cleaning, repair, and testing as follows: (A) Each tool shall be thoroughly examined for defects. B) If a defect or contamination that could adversely affect the insulating qualities or mechanical integrity of the live- line tool is found, the tool shall be repaired and refinished or shall be permanently removed from service. If no such defect or contamination is found, the tool shall be cleaned and waxed. C) The tool shall be tested in accordance with paragraph (i)(2)(iii)(D) and (i)(2)(iii)(E) of this section under the following conditions: After the tool has been repaired or refinished; and. After the examination if repair or refinishing is not performed, unless the tool is made of FRP rod or foam- filled FRP tube and the employer can demonstrate that the tool has no defects that could cause it to fail in use. D) The test method used shall be designed to verify the tool's integrity along its entire working length and, if the tool is made of fiberglass- reinforced plastic, its integrity under conditions. E) The voltage applied during the tests shall be as follows.
Other tests that the employer can demonstrate are equivalent. Note: Guidelines for the examination, cleaning, repairing, and in- service testing of live- line tools are contained in the Institute of Electrical and Electronics Engineers Guide for In- service Maintenance and Electrical Testing of Live- Line Tools, IEEE Std 9. View this flyer in PDF Format. Click here to Add Your Name To Our Mail List. View product literature on WAXING hot sticks and booms. View product literature on cleaning and treating HOT STICKSView literature on cleaning and treating TELESCOPING BOOMSView the Technical Talk article on live- line tool performance problems. Ask for Polywater® products by name at your local authorized distributor.
Home |. Translations |. Jobs. 11. 22. 2 6. ST N | Stillwater, MN 5.
USA1- (6. 51) 4. 30- 2. Voice) | 1- (6. 51) 4.
Fax)1- (8. 00) 3. Toll- Free US/Canada Only)Copyright © 2. American Polywater Corporation | 6/5/1.